System type: Pumped - differential control
System not working.
No power to outlet at which the controller was connected.
Used extension cord to test controller from another receptacle that had power. Very loud (clang) pump when turned on. Pump defective.
Controller and sensors tested fine.
Client stated that water was not hot enough. Raised tank element to 130 F - top and bottom.
Anti valve stuck at 3.