System type: Pumped – differential controlled
System is operational.
Controller tester indicates all modes are working. Sensor readings are reasonable.
Anti-scald valve stuck but operating.
Leak at collector pressure relief valve. Freeze valve metal parts rusting.
Gaps in insulation exposing copper piping.
Standard pitch pans do not appear to have been used at roof.
Insulation facing in collector is coming off.