System type: Pumped - timer control
System not working.
Check valve appears to be clogged and restricting flow. Timer was not operating. Needs to be reset.
Pressure relief valve on roof did not reseat after being opened to test pressure. Was able to reseat after working on it. Needs to be replaced.
Instructed client to change check valve and to obtain simple timer. Client appears to be capable of doing this himself.