System type: Pumped – differential controlled
System is working.
Anti-scald valve stuck.
Metal parts of valves on roof are rusting.
Air vent port is clogged with sediment build up.
Feed/return line pitch pan sealant had cracks and openings for moisture penetration.
Sloppy sealing at roof penetrations.